Water Heater Relief Valve
Water Heater Pressure Relief Valve
Are you looking for information on water heater relief valve? On this
page you'll learn what a hot water heater relief valve is, how to check it,
how to replace it and what you should do if its opening on its own.
Temperature and pressure relief valve.
Also known as- t&p valve (temperature and pressure) valve
and tpr valve (temperature pressure relief) valve.
Water heater pressure relief valves
are safety devices designed to relieve
pressure from a water heater in case
of extreme temperature/pressure rise.
Water expands as it is heated.
If a water heater thermostat
malfunctions and continues to heat
water non stop the tank would
eventually explode if it didn't have a
relief valve to relieve the pressure.
Water heater relief valve problems
Why is water slowly leaking out of the relief valve discharge (drain) line?
The pressure relief valve itself may be the problem, especially if its
an older valve.
Relief valves will release water slowly if their is to much pressure in the
tank. This happens on closed water systems ( check valve somewhere
in the system).
First replace your relief valve if it is an older one. If the new valve is allowing
water to leak out you may need to install an expansion tank on
the cold water inlet line near your water heater.
Expansion tanks are designed to absorb the pressure from your water heater.
The water pressure regulator valve may be at fault.
Why is my relief valve sporadically releasing large amounts of water?
This happens when the valve is opened because of high temperatures.
Replace faulty thermostat.
How to check a tpr valve.
1. To check for a leaking valve feel
the drain line with your hand to see if
its hot (see pic). The drain line may
be warm near the valve, this is normal.
If the line is hot the relief valve is opening.
2. Raise the test lever on the
relief valve (see pic).
You should hear water discharging
out the relief valve drain line.
If you do then your valve is working
If you do not hear a discharge or
your test lever won't raise (don't
force it) replace the relief valve
as soon as possible.
Check your water heater relief valve at least once or twice a year
to be sure its working properly.
How to replace a water heater pressure relief valve
Electric water heater - turn the water heater breaker off.
Gas water heater - set the temperature knob to its lowest setting.
Turn the control knob to the pilot setting.
Turn the water supply off at the water heater.
Open the nearest hot water faucet to relieve the pressure on the tank.
If the pressure relief valve is mounted on the side of the tank you'll have
to drain the tank until the water level is below the valve.
If the relief valve is mounted on top of the tank your ready to start.
Remove the drain line that's
attached to the relief valve.
Cut the line and unscrew it
from the relief valve.
You can remove the relief valve
with an adjustable wrench. Tap the
end of the wrench with a hammer
to loosen the valve.
Remove the old relief valve
Use telfon tape or pipe dope
and install the new relief valve.
Reinstall the valve drain line.
If your drain line is cpvc pipe
be sure to use cpvc glue to
couple the line together.
Allow the glue to dry 2 hours
before testing the new relief
Refill the water heater. Leave
the hot water faucet open until all the air is out of the line.
Check for leaks.
Electric water heater - turn
the power on.
Gas water heater - set the control knob to the on position.
Turn the temperature control knob to the normal setting.
If your looking for water heater relief valve for sale, check your
old valve for btu, pressure and temperature rating.
Return from water heater relief valve to water heater repair guide home